Minimizing Water Consumption and Overall Facility Improvement
The end-user was looking for a Belt Press replacement with an alternative dewatering technology.
Thanks to the cooperation with our UK municipal market distributor, Evergreen Water Solutions, we have conducted an on-site pilot test.
During the pilot trial, VOLUTE Dewatering Press has reached some magnificent results in performance.
The end-user replaced the belt press with VOLUTE Dewatering Press ES-354 model which is equipped with 4 x φ 350 cylinders.
Thanks to the clog-free construction, there has been a huge savings on rinsing water compared to the previously installed Belt Press.
Moreover, the operator had to be present on-site during the operation of belt press; currently the VOLUTE dewatering solution ES-354 runs under automated operation which doesn’t require operator´s constant attention.
Generally speaking, the work environment changed for the better and the end-user is very happy with their decision.
|Solids Concentration:||0.9 %|
|Flow Rate:||26.6 m3/h|
|DS Throughput:||240 kg-DS/h|
|Cake Solids Content:||20 %|
|Capture Rate:||96 %|
|Polymer Adding Rate:||0.9 %|